Translates radio signals from XPander detectors to the fire control panel
Built-in loop isolator
Diversity aerial design for improved signal integrity
XPander incorporates entirely new designs with respect to the wireless communication system. A Radio Interface is connected to the loop. It communicates with the control panel using the Apollo addressable two-wire power and communications system. The interface communicates with the detection and alarm signalling devices by means of radio waves.
The detectors are multistate in that they report normal, pre-alarm, fire or fault states to the radio base which transmits the information to the interface. The detectors incorporate drift compensation and report any compensation limit occurring.
The radio bases and signalling devices are addressable and use a pre-set analogue value to report via the XP95 or Discovery protocol. Apart from normal and fire the bases can send pre-set analogue values to indicate low battery, detector contaminated, detector tamper and low signal strength fault conditions.
loop-powered interface operating on 868MHz
wireless addresses seen by control panel as normal addresses
radio base with wireless circuitry and battery compartment
chamber designed to inhibit dirt penetration and thus reduce false alarms
automatic drift compensation with DirtAlert™ warning
algorithms for transient alarm rejection
FasTest™ reduces time taken to test detectors
remote test facility
3-5 years battery life
The XPander Diversity Interface is connected to the loop and provides communications from the control panel to the wireless devices and vice versa.
Features of the XPander Diversity Loop Interface are:
It is powered from the loop.
A maximum of five interfaces can be connected to a loop.
Up to 31 radio devices can be logged on to each interface.
The current drawn from the Interface should be taken into consideration when calculating the total load of a loop.
The XPander Diversity Interface has an integral LCD display which gives information on the state of the wireless detectors. The Diversity Interface transmits and receives signals via the integral Diversity Aerials which require no adjustment or maintenance.
The XPander interface aerial must be installed at least 400mm away from any metal object. The recommended minimum distance to any electrical equipment is 2 metres in all three dimensions.
An 8-segment DIL switch is provided for the address of the Interface to be set. When polled by the control panel, the XPander Interface returns a pre-set analogue value of 16 in normal condition.
Fire detection systems are life-saving systems and must, therefore, be highly reliable in use. Radio communications have been developed to a point where high reliability can be guaranteed, provided that the rules for the design of radio systems and installation are carefully observed.
Radio communication technology in the detection has matured to the point where a standard has been drawn up as part of the EN54 family of standards for components of a fire detection system. The standard is EN54 Part 25.
The frequency used by XPander is 868MHz which is the harmonised European radio frequency.
Name : Apollo XPander Alarm Control Panel Monitor Module - For Control Panel - White - ABS Plastic, Apollo Fire Detectors, ADI UK, Apollo