Please upgrade to the new Edge browser, or use Chrome, Firefox or Safari, before continuing. Internet Explorer will not support the best shopping experience on the ADI Digital Branch site after March 12, 2021.
All devices are powered directly from the loop and need no external power supply. They operate at 17-28V DC and are polarity sensitive.
A nominal sound output of 100dB(A) is achieved at a current consumption of 5mA in the case of the sounder and 8mA for the sounder beacon. Many control panels will be able to drive up to 20 sounders and up to 15 sounder beacons per loop on average. The maximum number of devices that may be connected to a particular loop should, however, be determined by a loop loading calculation using the Apollo Loop Calculator. This is available via the Apollo website www.apollo-fire.co.uk.
Since the alarm devices are intended for use in open areas, it is possible for more than one device to be audible at any given point in a building. For this reason, the operation of all may be synchronised by the control panel.
All the alarm devices can be assigned group addresses as well as individual addresses, so that the functional options of the sounder are identical with those of the Sounder Control Unit part no 55000-582 or 55000-182 (DIN-rail version).
The alarm devices have a base which is fitted to the mounting surface and wired as a 'first fix'.
The open-area alarm devices respond to their own individual address set with a DIL switch. They can also respond to a 'Group Address' which allows multiple sounders to be controlled simultaneously. A group address may be any spare address between 112 and 126 and is selected by means of a 4 segment DIL switch. A device under group address control must have an individual address between 1 and 111 otherwise a fault value of 4 is transmitted. Devices not using the group address facility may be addressed at any address (1-126).
XP95, Discovery and CoreProtocol compatible
The alarm devices will operate only with control equipment using the Apollo protocols. The features of the Open-area alarm devices are available only when the device is connected to a control panel with the appropriate software.
The Intelligent Open-Area Sounder has been designed for use in open areas and can be connected to any Discovery or XP95 system.
Self-test fault monitoring
Choice of tones on standard device: Apollo, Slow Whoop and DIN
Two volume settings 92dB(A) and 100dB(A)
Synchronisation of tones
Individual and group addressing
Built in isolator
Red or white options
Category : Addressable Systems, Fire & Gas Detection, Horn Spares, Products